SOPs Operating Procedure of Air Handling Units and Ventilations Units
To lay down an Operating Procedure for Air Handling Units, Exhaust, Supply and Ventilation Units.
This Standard Operating Procedure is applicable to the formulation plant of Pharmaceutical Company.
3.1 The Concerned Technician shall follow the Operating Procedure as per this SOP
3.2 The Officer/Executive-Engineering shall be responsible for implementation of the procedure as per this SOP.
Head-Engineering/Designee shall ensure the compliance of the procedure as per this SOP.
5.0 Abbreviations and Definitions
BMS: Building Management System
DDC: Digital Display Control
MCC: Machine Control Center
RH: Relative Humidity
VFD: Variable Frequency Drive
RA: Return Air
AHU: Air Handling Unit
6.1 In Manual Mode
6.1.1 Pre Startup Checkup
184.108.40.206 Ensure Power supply shall “ON” from MCC panel for all Air Handling Units, Exhaust and Supply and Ventilation Units.
220.127.116.11 Ensure Chilled Water and Hot water circulation is going on. Working Pressure of Chilled water and Hot water shall be more than 1 Kg/Cm2.
18.104.22.168 All VFD’s and Starters shall be in Manual/Local mode.
6.1.2 Starting Procedure
22.214.171.124 Start the core corridor AHU’s along with exhaust unit to maintain positive pressure in core corridor.
126.96.36.199 Start the all other AHU’s along with ventilation units after 10 minutes of Core Corridors AHU’s and Global Exhaust Units.
188.8.131.52 Record all the data after every three hours as per Annexure-I.
6.2 In Auto Mode
6.2.1 Pre Startup Checkup
184.108.40.206 Ensure Power supply shall “ON” from MCC panel for all Air Handling Units, Exhaust and Supply and Ventilations Units.
220.127.116.11 Ensure Chilled Water and Hot water circulation is going on. Working Pressure of Chilled water and Hot water shall be more than 1 Kg/Cm2.
18.104.22.168 All VFD’s and Starters shall be in remote/auto mode.
22.214.171.124 UPS power supply to BMS and all DDC panels shall be “ON”.
6.2.2 Starting Procedure
126.96.36.199 All AHUs, Global Exhaust, Global Supply and all ventilation Unit shall start through BMS which is Programmed for as per following sequence:-
188.8.131.52 Core Corridor’s AHUs and Exhaust Unit shall start before 10 minutes of other AHUs as scheduled.
184.108.40.206 After 10 minutes all other AHUs, Supply and Ventilation Units shall start as scheduled.
220.127.116.11 All AHUs are programmed for Design Temperature and RH settings. If there is any change in room condition requirement then Engineering-Executive/ Officer can only change the setting.
18.104.22.168 There are three level securities Password in BMS login.
22.214.171.124 One is primary level for operator. Operator shall be authorized for data checking only he can also take printout of data like RA Temperature, RH.
126.96.36.199 Second level is for Engineering persons who can change the:
Room condition settings.
Change in Alarm setting.
To make new login for Operators
188.8.131.52 Third level is for Administrator. In this level only ABB Engineer is authorized to change all setting, Change password of Second Level and reprogram the system.
184.108.40.206 Record all the data after every three hours as per Annexure-I.
7.0 Forms and Annexure
Logbook: Annexure – I
8.1 Master Copy: Documentation Cell
8.2 Controlled Copies: Engineering, Quality Assurance, Quality control, Production, Warehouse, Administration and House Keeping.
Reason for revision